discount 70% in 2018-10-18 to 2018-10-20
price: USD$ 3850.00
freight :USD$7.00,(Postal parcel)
Search Similar or mail to saler or send message to saler
Brand: SAGTAR(trademark owned by Santak Electronics Co., Ltd.)
Origin: Shenzhen, China
The Santak castle series C6K (S) ~3C20KS parallel redundancy uses double conversion online architecture, which can effectively solve all the power supply problems of the architecture design. The architecture can effectively block the impact of abnormal power on the load, but also ensure the stability of the output power, reliable, so that the safe operation of the load. Digital control technology is used to realize the function of parallel expansion and parallel redundancy, which provides users with flexibility and security guarantee for power supply planning.
1.High reliability parallel expansion technology allows you to plan more flexible power supply
In the past, you have planned large capacity UPS devices in the early days because of the expansion of the equipment in the future, which is a great waste. Now, as long as you consider your actual power requirements, it's possible to plan a proper UPS. In the future, if the expansion of the equipment needs the corresponding power expansion, only need to buy the expansion part of the UPS, parallel to the original power supply system, it can increase the flexibility of planning, and greatly reduce the waste of investment.
2.N+1Parallel redundant planning provides you with reliable power solutions
N+1 parallel redundancy means that there is one more UPS at any time to provide protection for your important equipment. Planning of power system, increase the capacity than the rated one, so that when the system in any UPS failure, can because of the additional one UPS, so that the power system can uninterrupted important equipment you provide high quality power, which makes the system more reliable. At the same time, the advanced current sharing technology makes each UPS share the load current in parallel operation, and improves the reliability of the system, but also prolongs the service life of UPS.
For example: the computer load is 20KVA, you can use 3 UPS to achieve parallel redundancy, if one of the UPS needs to be removed or shut down to dismantle. The other two UPS will immediately support all the loads. Therefore, no matter which UPS is out of order, it will make the valuable equipment get uninterrupted high quality power supply because of your proper parallel redundancy planning.
3.The compact design, saving land office space for you
Due to the application of advanced control technology, the power density is greatly improved, and the new C6K (S) ~3C20KS parallel redundant UPS is small in the same capacity of the online UPS. In today's land office space, save valuable space for you.
4.The design of online maintenance does not require power outage even if it is maintained
As long as the UPS to the maintenance mode, online maintenance safety you can load in a continuous supply condition; if you do N+1 redundancy parallel programming, even at the time of repair, power interruption, high-quality power supply equipment you can get valuable uninterrupted.
5.Intimate function design, make you more convenient to use
DC startup function allows you to use UPS without power supply. The function of the timing switch eliminates the loss caused by forgetting to use the UPS. Remote monitoring function to achieve the goal of unmanned. Powerful charging function, not only convenient for you to extend the standby time, intelligent charging way to make the battery life can be extended, save money. Auto restart function, so you don't have to boot UPS automatically after UPS standby shutdown. There are many other intimate designs to bring more convenience to your work.
6.Excellent technical indicators, so that you use more reassuring
All along, the Santak products are followed by strict international design specifications, allowing you to enjoy the quality of product performance.
Close to 1 of the input power, greatly reduce the pollution of the city power grid, improve the utilization of the power grid, is the green power supply.
Ultra wide input voltage range, in a variety of harsh power environment, for your valuable equipment to provide perfect protection.
Close to 90% of the full load efficiency, effective for you to save electricity costs.
Strong anti-interference ability, in line with the IEC61000-4 for electromagnetic interference requirements, can effectively eliminate the noise on the grid, high voltage, sudden wave, to your equipment to provide a clean power environment.
Other excellent technical indicators allow you to enjoy high quality at an affordable price.
７.Intelligent power monitoring and management softwareWinPower2003
Supporting the MicrosoftWindows95/98/Me/NT/2000/XP/Linux operating system. Suitable for TCP/IP network, support TCP/IP UPS network monitoring provides a hierarchical directory structure; management network UPS; abnormal event occurs through radio, email, pager and mobile phone text messages to inform the user; automatic detection of UPS type and communication port; provide the password protection function; support timing on / off UPS support UPS timing function; self testing function; support graphics real-time display UPS function; support network close multiple servers and workstations; to support the SmartEvent function, the user receives the abnormal information according to their own definition of power demand way; most applications support closing and preservation of the relevant documents; Jane, Chinese support / traditional multi language and English platform; support online help function. With data recording (including city power, UPS, load, battery) and event log function, it is convenient for the system administrator to maintain the UPS routine.
８.Complete monitoring and communication function
It provides RS-232, intelligent socket (IntelligentSlot) and other monitoring communication interface. Users can choose the Santak AS400 card, to provide IBMAS400 standard communication signal, to make RemoteDisplay, including sound alarm and light display and other monitoring functions. Or buy the Santak WebPower smart card, through the Internet Internet for global management, or through the SNMP network management, centralized monitoring and remote monitoring functions.
●High frequency on line series built-in external battery charger, users can configure different capacity batteries according to their own needs.
●The overload and short circuit protection of advanced design is durable and reliable.
●Built in network control interface, can be equipped with stand-alone or network version of 3CNDONUPS automatic save software
●Electronic control circuit adopts micro processor to further improve the reliability and stability of UPS.
UPSThe use of
1)Normal boot sequence
There is a shock current due to the general load at the starting instant,andUPSThe internal power components have a safe working area,Although we have a certain margin when choosing devices,However, excessive impact current will shorten the service life of components, and even cause damage to components. therefore,In use, the damage caused by impulse current should be minimized.
Boot sequence:First send the electricity to the cityUPS，UPSSwitch on and make it in working state. Load the load one by one,Load with large impulse current first,Load with small impulse current.Never load all the loads at the same time,Also can not be loaded with the boot.
The shutdown sequence is as follows: first closes the load one by one, and then the nextUPSPanel shutdown,sendUPSThe charger continues to charge the battery pack when it is in bypass. if necessaryUPSNo output, will beUPSShut down completely,Then you can disconnect the input power.
UseUPSWhat are the matters needing attention?
1）UPSThe use of the environment should pay attention to good ventilation, conducive to heat dissipation, and keep the environment clean.
2Do not bring inductive load, such as currency counter, fluorescent lamp, air conditioner, etc., so as to avoid damage.
3）UPSOutput load control at60%Right and left, reliability.
4）UPSCarrying too light (for example)1000VATheUPSbelt100VALoad may cause deep discharge of the battery, will reduce the service life of the battery, should be avoided as much as possible.
5Proper discharge will be helpful to the activation of the battery, such as long time no power supply, and the power consumption should be cut off every three monthsUPSWith a load discharge once, this can extend the service life of the battery.
6For most smallUPSGo to work againUPSWhen starting, avoid starting with load and turn off at workUPSFor the network roomUPSBecause most networks are24Hours work, soUPSIt has to run all weather.
7）UPSAfter discharging, the battery should be charged in time so as to avoid the damage of the battery due to excessive self discharge.