discount 70% in 2018-09-21 to 2018-09-23
price: USD$ 174.30
freight :USD$7.00,(Postal parcel)
Search Similar or mail to saler or send message to saler
1. Working power supply:220VAC，50/60HZ 2. Constant temperature range:+5~+35℃
3. Standard load:<3A 4. Power waste：<1W
5. Temperature sensing element:NTCThermistor6. Temperature control accuracy: +1.0℃
7. Shell material: whitePC/ABSFlame retardant material8. Outline size:86*86*13（mm)
9. Work environment:- 10~+60℃ 9. Installation:86Standard cassette
10. Transport storage environment: temperature:-20~+70Temperature, relative humidity:RH<92%
Three. Main functions and characteristics
3.1 liquid crystalLEDdisplay
3.2 Four kinds of wind speed settings, low, medium, high and automatic wind.
3.3 Temperature resolution:1℃。
3.4Relay contact form output.
3.5 With communication interface, can be remote or centralized control.
3.6 Power off memory function: memory: mode, switch machine status, setting temperature, wind speed, address code, etc..
3.7 Fault diagnosis: short circuit display of sensorE1Open circuit displayE2. When the fault occurs, the valve is turned off.
Four, LCD display
First power on, off state
Boot state, display contents include: working mode, setting temperature, environmental temperature, communication address and fan status.
1） Working mode: two control products are available2Mode: heating and cooling; users can set it by mode keys. When the factory is out, the working mode is cooling mode.
2） Setting temperature: setting range is+5The temperature can be adjusted by increasing the temperature and lowering the temperature at the temperature range from +35 to C. When the factory is set, the temperature is 22 degrees centigrade. Step 1
3） Room temperature, the display temperature is 0 HI ~+95, when the room temperature is less than 5 degrees, showing LO; when room temperature is greater than 95 degrees, display the temperature.
4） Mailing address，Setting range is0000~FFFFIt can be adjusted by the expert mode key, and the user can modify it at will!
5） Fan status, including automatic identification and fan speed, can be set by fan keys. At the factory, the fan speed is high.
Automatic wind speed：
Cooling state: when room temperature-Setting temperature >2 DEG C: valve opening, running high speed wind;
When room temperature-setting temperature≥1℃、≤2Temperature: the valve opens, runs medium speed wind
When room temperature-Setting temperature <1 DEG C: valve opening, running low speed wind
When room temperature-setting temperature>1 temperature: valve shut off, fan delay stop (fan controlled)
Heating state: Contrary to refrigeration
Five. Key operation instructions
5.1 User button description
Switching mode: heating/refrigeration
Increase setting temperature
Wind speed key
Switch fan stalls: low/in/high/automatic
Reduce setting temperature.
Switch status: boot/Shutdown
Note: under the condition of startup, press the button at the same time"▲”+“▼”6SYou can lock the temperature control/Unlock
5.2Expert mode button description:
Long press in shutdown6SThe mode key is entered into the first level menu, adjusted by the expert mode, and then the parameters of each menu are adjusted by adding and decreasing keys:
Factory defaults to0°
Fan controlled setting
OFFFan is not controlled
Factory defaults toON
Two control/Four control options
Factory default two control
Device address code low setting
Factory defaults to33
Device address code high setting
Factory defaults to10
Users can not do this at will, otherwise it will affect the normal use!!!
Six. Installation instructions
6.1 Be sure to install the device after power failure, otherwise it will damage the system components easily.
6.2 Select the correct installation position (about height from the ground)1.6Don't install the product in direct sunlight or moist position.
6.3 Altitude: no more than2000M.
6.4 If you install it in the toilet, please use a special waterproof mask.
6.5 According to the wiring diagram, according to the needs of the power board485Twisted pairA、BThe wire, the zero line, the electric valve and the fan coil are all connected correctly.
6.6 The power supply board and liquid crystal board is opened, screw the power board of the shell is fixed on the embedded cassette box. Pay special attention to the direction of the enclosure.
6.7 Clip the LCD panel into the open power panel.
6.8 After installation, electrify test.
Seven, product function overview
7.1 Valve status
Two control, with three line control valve or three line two control valve - valve control width is +1When the room temperature is smaller than the set temperature1When the temperature is higher than the setting temperature, the valve is opened1At temperature, the valve is closed; others
In case, the valve maintains its original state.
Four control, with three lines and a control valve, cold water valve is in the closed state, the control width of hot water valve is +1C. When the room temperature is smaller than the set temperature1When the temperature is higher than the setting temperature, the hot water valve is opened1When hot, the hot water valve is closed; in other cases, the hot water valve maintains its original state.
Two control, with three line control valve or three line two control valve - valve control width is +1When the room temperature is greater than the set temperature1When the temperature is lower than the setting temperature, the valve is opened1At temperature, the valve is closed; in other cases, the valve maintains its original state.
Four control, with three lines and a control valve, hot water valve is in the closed state, the control width of cold water valve is +1C. When the room temperature is greater than the set temperature1When the temperature is above the set temperature, the cold water valve is opened1When the temperature is cold, the cold water valve is closed; in other cases, the cold water valve maintains its original state.
3After shutdown, the valve is turned off.
7.2 Fan status
The user can adjust the height, middle, low or automatic shift of the working gear through the fan key; in the automatic file, the product automatically adjusts the fan stalls according to the room temperature and the setting temperature.
Fan controlled: when the valve is closed20SAfter that, the fan is closed. Not controlled: the wind machine is working non-stop.
When the factory is out, the fan is controlled, that is, when the valve is closed20SAfter that, the fan is closed.
After shutdown, fan low air operation20SAfter closing.
Eight, beltRS485Communication specification(see communication protocol)
Please make sure that the product is installedThe shielded twisted pair line,And485Twisted pairAThe B terminal is connected correctly according to the wiring diagram. Communication protocol as standard485Protocol, the expert can adjust the device ID through the expert mode key, and refer to the expert button for specific operation.
Nine. Simple exception handling
Please confirm again whether the fire line and the zero line are connected correctly; whether the setting of the air conditioning and heating mode is consistent with the requirements.
Power on display OFF
Switch key not opened
Click on the key
No power on display
Incorrect access to FireWire L;
Incorrect access to zero line N
Ensure correct access to the power terminal
LCD motherboard and driver
Loose line between power supply
The actual wind speed is inconsistent with the display
High, medium and low terminal wiring order error
Check external line drawing
The cables are not connected properly or loose
Check external lines
Room temperature (test temperature) deviation
Temperature not corrected
Recalibration of measurement temperature
Installation position is not
Improve installation environment
Ten, matters needing attention
10.1The controller must be equipped with power control equipment. If the controller is not used for a long time (more than one month), the power supply which is connected to the controller will be cut off.
10.2 The controller should be installed by professional technicians in accordance with the instructions.
10.3 Please do not install the controller near the high temperature heat source or harsh environment.
10.4 Before installation, make sure that the power supply is in accordance with the voltage indicated by the controller.
10.5 Please read the instructions in detail and use this product.
10.6SelectionRS485Communication time,A、BMake sure you use a shielded twisted pair line interface, otherwise communication will not work properly.
10.7 A、BBe sure to use connected series structure, namely after a previous one to Tsu, the star and tree, ring connection is not allowed.